One hundred fifty percent spare fuses shall be supplied. Fuses shall
be supplied in standard commercial boxes of five with a minimum
quantity of 15 fuses.
Do not provide where installed in a subassembly for which a repair
part is provided.
One for each 10 or fraction thereof installed.
Repair parts for linear movement switches shall consist of the complete
assembly (item 33 in table V) and the subassemblies (modules and parts
as specified in the applicable specification sheet of MIL-S-24187.
Quantities to be supplied for each subassembly or part shall be as
specified for the comparable item in table V.
Two for each 100 or fraction thereof installed.
One of each type of tool required to crimp, insert, and remove the
removable contacts provided under item 5. See table VI.
Provide one complete set of each type of tool for each switchboard.
These tools shall be designated 0SI. See table VI.
Repair parts set for switching unit power transfer shall be in accord-
ance with MIL-S-17773.
Bus failure alarms which are covered by applicable drawings or which
appear in the Federal Supply Catalog are not required to be furnished
as repair parts.
Only those meters which are used with power conversion equipment con-
trolled from the I.C. switchboards and which are not listed in the
Federal Supply Catalog are required to be furnished as repair parts.
Panel Mounted Assembly Test Cables shall be in accordance with
Drawing 803-5002567: 1 each cable assembly (as required) to be
supplied for each switchboard.
3.10 Panel-mounted assembly test cables. Test cables capable of connecting
removed panel-mounted assemblies to their associated circuits for maintenance and
troubleshooting shall be provided for each switchboard (panel assemblies con-
taining series "AN" connectors do not require test cables) in accordance with