(1) ON/OFF Camera motor power switch operation.
(2) Clock operation.
(3) Verify proper Film Low Indicate Signal.
(4) Displays test.
Verify elapsed time indicator operation.
C&D TS elements. Unless otherwise specified herein, elements of the
C&D TS shall be installed or stored in rack-and-panel type cabinets.
Console, Test, Control-Display-Dop pler Filter OJ 251()/AWM-23(V).
The equipment of this console shall be as specified in the following.
Panel, Power Distribution SB-3695()/AWM-23(V). The power dis-
tribution panel shall provide the capability to:
Control the test station power function.
Indicate that input power forms are applied to the test station.
Provide overload protection for the test station.
Display test station malfunction indications.
Digital multimeter. A digital multimeter, Systron-Donner 9340-5B,
or equivalent, shall be supplied and shall provide capability to perform ac
and dc voltage, and resistance measurements.
Counter/timer. A counter/timer, Systron-Dormer 6038-EE-10A, or
equivalent, shall be supplied and shall provide capability to perform freqency
and time interval measurements.
Switching Unit, Fault Isolation SA-1894()/AWM-23(V). The fault
isolation switching unit shall provide capability to perform the fault isolation
switching during fault isolation tests of the WRAs and during test station self
The mounting shall serve as a
holding fixture for Display, Detail Data IP-1111()/AWG-9, IP-1173()/AWG-9
and IP-1185()/AWG-9 and shall provide electrical connections for the WRA.
Mounting MT-4499()/AWM-23(V). The mounting shall serve as a
holding fixture for Display, Tactical IP-1110()/AWG-9, Control, Sensor
C-9037()/AWG-9, Control, Computer C-9036()/AWG-9, and Control, Sensor
C-9035()/AWG-9 WRAs. The assembly shall also provide electrical and
cooling air connections for the WRAs.