3.10 Technical repair standard. A technical repair standard (TRS) shall
be provided upon initial introduction of a new equipment or introduction of an
equipment that has an approved TRS if major or minor configuration changes have
been approved that would effect the adequacy of the standard for use in new
equipment repairs (see 6.2.2).
3.10.1 TRS technical content shall include sufficient technical details
to enable a repair, maintenance, or overhaul activity to restore the equipment's
dimensions, clearances, and tolerances such that the equipment is capable of
performing its function as originally specified and is capable of being logisti-
cally supported by the DOD logistics support system.
3.10.2 The TRS format and content shall conform to DOD-STD-2147 and shall
be approved and validated in accordance with this standard.
QUALITY ASSURANCE PROVISIONS
4.1 Responsibility for inspection. Unless otherwise specified in the
contract or purchase order, the contractor is responsible for the performance
of all inspection requirements as specified herein. Except as otherwise
specified in the contract or purchase order, the contractor may use his own or
any other facilities suitable for the performance of the inspection requirements
specified herein, unless disapproved by the Government. The Government reserves
the right to perform any of the inspections set forth in the specification where
such inspections are deemed necessary to assure supplies and services conform to
4.1.1 Inspection system. The inspection system which the contractor is
required to maintain, as provided in the inspection clause of the contract or
order, shall be in accordance with MIL-I-45208 (see 6.2.1). The completed parts
examination (see 18.104.22.168) shall fulfill the completed articles inspection
requirements of MIL-I-45208 (see 6.2.1).
22.214.171.124 The inspection system shall include a completed part examination
procedure whereby each functionally and dimensionally critical part and assembly,
including the final product, is examined on completion in accordance with a
completed part examination check list accompanying each part or assembly
126.96.36.199 A copy of the completed part examination check list for the
completed pump, identified by manufacturer's serial number, shall be furnished
the contracting activity (see 6.2.2) in duplicate for each pump. On these
copies the contractors quality control manager shall certify that the
inspection requirements specified herein have been fulfilled and that the unit
is in accordance with the approved drawings and the applicable specifications.
4.1.2 Variations. No variations or deviations from approved design
drawings in 188.8.131.52 shall be permitted.